0.6/1kV Overhead Insulated Conductor
★ Product standard
This product is manufactured according to GB / t12572-2008 "overhead insulated cables with rated voltage of 0.6/1kv and below" and iec60502 "extruded insulated power cables and accessories with rated voltage of 1-30kv".
★ Usage characteristics
2.1 rated voltage (U0 / U): 0.6/1kv
2.2 the allowable long-term working temperature of cable conductor shall not exceed:
PVC, PE insulated overhead cable: 70 ℃;
XLPE insulated overhead cable: 90 ℃;
2.3 in case of short circuit (the longest duration shall not exceed 5S), the maximum allowable temperature of cable conductor shall not exceed:
PVC insulated overhead cable: 160 ℃;
Polyethylene insulated overhead cable: 130 ℃;
XLPE insulated overhead cable: 250 ℃
2.4 the ambient temperature during cable laying shall not be lower than - 20 ℃.
2.5 allowable bending radius of cable:
When the outer diameter D of the cable is less than 25 mm, it shall not be more than 4 times of the outer diameter of the cable.
When the outer diameter D of the cable is equal to or greater than 25 mm, it shall not be greater than 6 times of the outer diameter of the cable.
2.6 when the cable is used in AC system, the rated voltage of the cable shall be at least equal to the rated voltage of the system; When the cable is used in the DC system, the rated voltage of the system shall not be greater than 1.5 times of the rated voltage of the cable.
|JKV||Copper core PVC insulated overhead cable||This product is suitable for AC 1kV and below insulated overhead power lines|
|JKLV||Aluminum core PVC insulated overhead cable|
|JKLHV||Aluminum alloy core PVC insulated overhead cable|
|JKY||Copper core polyethylene insulated overhead cable|
|JKLY||Aluminum core polyethylene insulated overhead cable|
|JKLHY||Aluminum alloy core polyethylene insulated overhead cable|
|JKYJ||Copper core XLPE insulated overhead cable|
|JKLYJ||Aluminum core XLPE insulated overhead cable|
|JKLHYJ||Aluminum alloy core XLPE insulated overhead cable|
|JKLGV||Aluminum alloy core XLPE insulated overhead cable|
|JKLGY||ACSR cored PE insulated overhead cable|
|JKLGYJ||ACSR cored XLPE insulated overhead cable|
Scope of production
|Model||Number of cores||Nominal cross section of conductor(mm2)|
|Copper conductor||Aluminium conductor|
Cable operation conditions
1. Laying in air
1.1 when the single core cable is laid in parallel, the center distance: 185 mm 2 or less is twice of the cable diameter, and 240mm 2 or more is 90mm.
1.2 ambient air temperature: 40 ℃
1.3 long term maximum operating temperature of Conductor: 90 ℃
2. Directly buried laying
2.1 When the single core cable is laid without contact, the distance between the center of the cable is twice the diameter of the cable.
2.2 soil temperature: 25 ℃
2.3 long term maximum working temperature of Conductor: 90 ℃
2.4 soil temperature coefficient: 1.0 ℃. M / W
2.5 direct burial depth: 0.7m
Cable installation and use
1. Cable selection
1.1 the rated voltage U0 / u (UM) of the cable is shown as: uo is the rated power frequency voltage between the conductor for the cable design and the ground or metal shield, u is the rated power frequency voltage between the conductors for the cable design, and um is the maximum value of the highest system voltage that the equipment can withstand.
1.2 according to the different laying environment and load of the cable, correctly design and select the type and specification of the cable. Non armored type is suitable for overhead, indoor, tunnel, cable trench and other occasions, and can not bear external mechanical force; The armored type can be directly buried underground under the same conditions as the non armored type, and can bear certain external mechanical force. Single core cable is not allowed to be laid in magnetic pipe. Special type of cable should be selected for inflammable and explosive, chemical corrosive, high temperature and low temperature.
2. Storage and transportation
During the storage of cables, the packaging shall be standardized to avoid long-term outdoor sun exposure, both ends shall be reliably sealed, long-term storage and humid environment are not allowed, and the cable reel cannot be placed horizontally. During transportation, the height of the plate should be considered and fixed effectively. During hoisting, several plates are not allowed to be hoisted at the same time, and it is strictly forbidden to push down from a high place.
3. Laying and installation
3.1 special tools such as pay off rack and guide roller shall be used for cable laying to prevent mechanical damage and keep away from heat source.
3.2 when the cable is laid through the pipe, the inner diameter of the pipe shall not be less than 1.5 times of the outer diameter of the cable. When multiple cables are laid through the pipe, it is forbidden to twist and squeeze the cable. The pipe has enough capacity, and the total area of the cable shall not exceed 40% of the total area in the pipe
3.3 the minimum temperature of cable laying shall not be lower than 0 ℃, and the bending radius shall not be less than 20 times.
3.4 when the traction conductor clamp is used for laying, the maximum allowable traction force is p = OA (n), a conductor section. O is 50N / mm2 (copper) and 30n / mm2 (aluminum).
After installation, the insulation resistance of the cable shall be tested without load. If necessary, AC power frequency withstand voltage test shall be conducted for 1min
Zhongxiang Photoelectric Technology Co., Ltd.
Service: +86-317-3362888 / 3362999 / 3318999
Address: Jinhua Road branch line, Renqiu Economic Development Zone, Hebei Province
Copyright © 2021 Zhongxiang Photoelectric Technology Co., Ltd. 冀ICP备********号